Netwater Technology, has carried out the renovation of the complete PRE-TREATMENT composed of the following equipment:
- SandTech®Nw210 sand classifier, to treat Qmax 25m3 / h, main construction material in AISI-316L. The original technology was an alternative camel-type classifier, which did not have a well dimensioned tank and there was no optimal retention time for the sands to settle, practically the flow of water and sand that entered the equipment through the inlet pipe, it came out through the outlet pipe, this generated serious problems in the rest of the WWTP processes and caused frequent failure of pumps, diffusers, etc…
NETWATER TECHNOLOGY, S. L.: placed great emphasis on designing a tank with the optimum volume for the sands to settle and the water to settle without sand, too. The pipes were designed at slightly special points due to the existing pipes on site and the installation was a great success.
Netwater Technology, through this installation, has managed to meet the needs of our client, as you can see in the images you can see the large amount of sand that the equipment supplied is being able to extract and in this way, contribute to a better performance of the treatment plant. and reduction of operating costs.
So that you can see the scope of the project we provide you with some images.